Design Criteria: 3' Frictional Pressure Drop per 100' Pipe Length with a Maximum Velocity of 10 ft/sec
Figure  1 Friction Loss for CLOSED Piping Systems: Schedule 40 Steel Source: Carrier Systems Design
style="display:inlineblock;width:728px;height:90px"
dataadclient="capub2352511885319423"
dataadslot="2380026829">
Design Criteria: 3' Frictional Pressure Drop per 100' Pipe Length with a Maximum Velocity of 10 ft/sec
Figure  2 Friction Loss for OPEN Piping Systems: Schedule 40 Steel Source: Carrier Systems Design
PLASTIC Physical Dimensions and Sizing Criteria (ASPE Data Book)
Design Criteria: 3' Frictional Pressure Drop per 100' Pipe Length with a Maximum Velocity of 10 ft/sec
Figure  3 Friction Loss for Copper Piping Systems: Types K, L, & M Source: Carrier Systems Design
ALUMINUM , BRASS Handbook for Mechanical Engineers : Baumeister & Marks
EL = L/D* D (EL = Equivalent Length. L=Pipe Length, D = Pipe Diameter)
Velocity Pressure Factor (K) forWater : K = C*D**E: Pressure Drop (PD) = K*VP
EL = L/D* D (EL = Equivalent Length. L=Pipe Length, D = Pipe Diameter)
Velocity Pressure Factor (K) forWater : K = C*D**E: Pressure Drop (PD) = K*VP
LOW PRESSURE STEAMPIPE SIZING CRITERIA : Flow Rates of Steam (lbs/hr)
HIGH PRESSURE STEAMPIPE SIZING CRITERIA : Flow Rates of Steam (lbs/hr)
CONDENSATE FLOWRATE (lbs/hr) Condensate Return Pressure = 0 psig
Example: 6800 lbs per hour of steam flow in a 2 ^{1}/_{2} inch pipe at 100 psig pressure.
What is the pressure (psi) drop per 100 ft length of pipe and the flow velocity?
Answer: psi/100' = 11 velocity = 32,000 fpm
Figure  17 Steam Flow Rates at Various Pressures and Velocities for Schedule 40 Pipe Source: ASHRAE
Downstream Pressure
For natural gas the nominal BTU/cf varies from about 900 to 1100 BTU/cf. In general it is common to set
in table above = pipe length + 50%
For natural gas the nominal BTU/cf varies from about
900 to 1100 BTU/cf. In general it is common to set



The capacity of a low pressure natural gas (less than 1 psi) pipe line can be calculated with the Spitzglass formula like
q = 3550 k ( h / l SG)^{1/2} (1)
where
q = natural gas flow capacity (cfh)  h = pressure drop (inWater Column) 
l = length of pipe (ft)  k = [d^{5} /(1 + 3.6/d + 0.03 d)]^{1/2} 
d = inside diameter pipe (in)  SG = specific gravity 
For natural gas the nominal BTU/cf varies from about 900 to 1100 BTU/cf . In general it is common to set
1 Cubic Foot (CF) = approx 1,000 BTUs
1 CFH = 1 MBH
The specific gravity of natural gas varies from 0.55 to 1.0 .
The downstream pressure in a houseline after the meter/regulator is in general in the
range of 7 to 11 inches Water Column, or about 1/4 psi.
Example  Natural Gas Pipe Capacity
The capacity of a 100 ft natural gas pipe with a nominal diameter 0.5 inches (actual ID 0.622 in )
and 0.5 inches WC pressure drop can be calculated as
k = [(0.622 in )5 /(1 + 3.6 / (0.622 in) + 0.03 (0.622 in))]0.117
q = 3550 0.117 ( (0.5 in) / (100 ft) 0.60 ) 1/2 = 37.9 cfh
Specific gravity of natural gas is set to 0.60.
Horizontal Fixture Branches and Stacks 
Building Drains and Sewers 


HORIZONTAL RAINWATER PIPE SIZING 
HORIZONTAL RAINWATER PIPE SIZING 
EnergyModels.com Instruction and Discussion for Energy Modelers, Building Simulators, Architects and Engineers
EnergyModels.com is a site for energy modelers, building simulators, architects, and engineers who want learn the basics, to advanced concepts of energy modeling. We've got online training courses and tutorials for eQUEST, Trane TRACE 700, OpenStudio, and LEED for energy modeling. All our energy modeling courses are video based. What better way to learn energy modeling software than screencasts of exactly how things are done?
Copyright © 20102013 CosmoLogic LLC. TRACE 700 and eQUEST are ™ of Trane Inc. and James J. Hirsch respectively. EnergyModels.com is built in San Francisco, CA and Slinger, WI USA.